When India’s leading drug maker Cipla decided to build a world class drug manufacturing plant at Goa, it chose the Danfoss VLT 6000 HVAC drives to control around 350 AHUs and 20 Pumps to maintain inside conditions and differential pressure in the manufacturing areas
Cipla, one of India’s top five pharmaceutical companies created news, stunned the global drug firms, when in February 2003 it offered to export a trio of AIDS drugs to the poor regions through the French Charity Medecins Sans Frontieres, at the lowest international price of $350 per patient, annually.
Cipla had its beginning in 1935 as ‘Chemical, Industrial and Pharmaceutical Laboratories’ and is today India’s third largest drug maker by market share with a turnover of $325 million in 2002. Headquartered at Mumbai in India, its range of products are manufactured in 18 state-of-the-art manufacturing facilities throughout the country. Its product range consists of tablets, capsules, liquids, injections, ophthalmic, topical and nasal preparations, inhalers and powders etc.
Cipla broke ground for their new state-of-the-art pharma manufacturing plant at Goa in 2001. Since the plant has to comply with US FDA, WHO, MCA, MCC, TGA and CGMP requirements, the emphasis was on quality. The Goa manufacturing plant consists of eight independent manufacturing areas – Units I to VIII.
Cipla decided to use double skin air handling units (AHU) to maintain the required inside conditions. Different type of fan options such as belt driven, direct coupled centrifugal, plug fans etc., were considered. Finally they zeroed in on direct driven plug fans to avoid problems of contamination of the manufacturing area because of belt dust, energy losses due to slippage of belts and minimise the maintenance and down time.
However, plug fans need to be directly coupled to the motor and to achieve the design air flow (CFM) required, the fan has to run at speeds above or below the nominal speed of the motor. That was when Variable Frequency Drives (VFD) were thought of and Danfoss proposed a solution with VLT 6000 HVAC series drives, specially designed for HVAC applications. Further more, VFDs gave them the flexibility to automatically maintain a constant CFM to the conditioned area irrespective of filter condition – without any user intervention (like manual operation of outlet dampers) – while at the same time providing them with high energy savings.
Selection of the right VFD
Cipla was very particular in selection of the equipment for their new plant for approval from international regulatory authorities for exports, such as MCA, MCC, TGA and USFDA etc. When it came to VFDs, the criteria for selection was the following:
Fitting the bill
The following features offered by the Danfoss VLT 6000 HVAC appealed to the project team which was headed by BB Shah.
Shah says, “When we compared various makes of VFDs for the technical qualification, we found that Danfoss was offering their HVAC specific model – the VLT 6000 HVAC. Now, that made sense to us. All of our concerns towards applying VFDs so extensively in the project were taken care of in this product. It had inbuilt harmonic filters and RFI filters. Usage of inverter grade motors were not required, which reduced our first cost. Further, it had also the provision to control the CFM output of the AHU in closed loop with a static pressure sensor, to be located in the duct. This was extremely useful for us in the plants, where we were not immediately implementing BMS.”
The electrical and instrumentation part of the project was lead by PG Patil, who appreciates the flexibility of the VLT 6000 HVAC drives. Patil, who currently is responsible for the electrical and instrumentation department says, “When we commissioned the VLT 6000 HVAC drives in 2001, we were amazed at its flexibility in operation. We used the following features of the drives at our plant, while commissioning the system:
Patil is upbeat about the energy savings achieved through the usage of VFDs. He shares his experience and says, “In most of the cases, the VFDs are operating 15 to 20 Hz below the design frequency. Now, without the VFD we would have naturally used a damper to maintain the constant CFM to the conditioned area and this would have saved no energy. This savings is very valuable to us and is helping to keep our operational costs under control. In Unit-I where we are logging the energy consumption on the BMS, we see that we are saving approximately 40 per cent of the energy compared to full speed operation. We have already recovered the cost of VFDs and BMS within a period of two years from the above energy savings.”
Application on pumps
The VFDs were installed on the chilled water pumping system also. In line with the criteria to achieve maximum energy savings, primary – secondary system of chilled water pumping was adopted. The VFDs were installed on secondary pumps whose speeds are modulated to maintain a set differential pressure across the supply and return headers under all load conditions. The pump ratings vary from 11 kW to 75 kW and are working round the clock to ensure optimal energy consumption.
Reliability in operation
The VFDs have been in operation from December 2001. In fact, Shah and Patil are now happy with their selection of their VLT 6000 HVAC. Since the plant operates continuously, the engineering department normally keeps a stock of essential spares. In accordance with the above, when Danfoss submitted a proposal for essential spares and standby VFDs, the same was not approved by the Engineering In-Charge AV Mahajan citing the fact that there have not been a single instance of failure of the VFDs. We need not say more about the reliability of VLT 6000 HVAC.
Emulating the success in the company’s other manufacturing locations
The Goa plant has been a trend setter in the VFD applications in Cipla. Further to the satisfaction derived from the Goa application, VFDs for AHUs have been applied on their other plants at Daman, Patalganga and Satara. In some of these plants, the VFDs, in conjunction with a differential pressure transmitter, work as a dedicated controller to maintain the positive pressure to be maintained between different manufacturing areas and corridors.
As of March 2004, Cipla group had 374 VFDs for AHUs and 23 for pumping applications. Furthermore, as many as 27 other VFDs are working in other pharma machinery applications inside the manufacturing area. This makes the biggest installation of VFDs for HVAC applications in India, totaling to more than 400 drives at a single location.